Manual. Description; Buy; Works with; Related models; More like this; Manufacturer. The Allen-Bradley ASB Remote I/O Adapter Module physically resides. The ASB/D remote I/O adapter module serves as an interface between . assembly and installation manual for your programmable controller or scanner. Remote I/O Adapter Module, ASB Series D, Product Data, Aug , ASB Series E, User Manual, Feb , UMA-US-P.
|Published (Last):||26 May 2006|
|PDF File Size:||10.49 Mb|
|ePub File Size:||14.47 Mb|
|Price:||Free* [*Free Regsitration Required]|
Product price, specification, warranty and availability subject to change without mahual. Let me take a stab at this I have been watching and reading various posts on this board for several years and have appreciated your and everyone else’s unselfish contributions and time sacrifice to help others.
Then we can point out where the error is. This is why we kept harping about dip switch settings. Your message when you did the autoconfig seems to bear that out. I could use but it is not neccessary. Please contact us to complete your request. That’s right, the one chassis could be using up to 4 racks. It’s like having the store come to you! Features Communication Rates from Ron brings up great points with using Auto-Configure to test the switch settings.
A series b and a series a RIO adapter. But I think it could also be a configuration issue. I did not tell you the configuration It is important to understand that chassis and rack in the PLC-5 mean different things. You can zoom in close to see the labels 1771-ab the serial number or zoom out to see the overall condition of the equipment. Manhal, an assumption since we don’t know. Unfortunately I am not going to be able to address this for another day or so but if you would kindly give me leave I will respond to you as soon as I have re-checked all of these.
Well, what if you were able to see manyal piece of equipment before you purchased manula No outputs 177-asb on of course – So what am I missing. If you are using 1-slot addressing for the remote chassis and it is configured for Rack 3 then Mike is pointing out that anything larger than an 8-slot chassis is useless.
Also double check the chassis dip switches. Mercury Drive Champaign, IL If not, do you have the switch settings? Unfortunately the only way to get the switch settings on the remote chassis is to remove power and pull out the adapter.
The ASB features include: Don’t forget the DIP switches on the remote chassis too. Oh, after more reading, I see there is a difference on backplane settings depending on what is in the chassis. I thought you had original B series manual. But we are risking things making that assumption. Switch 6 was the problem Having the program might help us identify how the local chassis is addressed but it doesn’t do much more than that.
Allen-Bradley ControlLogix User Manual: Configure 1771-asb Adapter
What cable are you using, did you properly terminate it? We appreciate your interest in using our InstraView website! How are the local chassis dip switches configured? S2 switches 2,3,4 should be off on the ASB and switch 1 should be on I will take another look at the switches but posting the entire program certainly is not neccessary.
Sir, I am not at all irritated and before anyone misjudges maual for an unwarranted outburst I will defend you.
One of our friendly Customer Service representatives will be contacting you shortly with information on when the equipment you requested will be available for viewing. You mention 1-slot addressing for the remote chassis so we can assume that the local chassis is also 1-sot. To this issue, Point to Point RS communication at baud is not at all slow with these processors for no more data than is being transfered.
Again, lots of assumptions. Please feel free to contact us at sales artisantg. Actually, that is very simple, in that configuration I use the RSc port and in spite of the stated limitation of 50′ the limitation depends on several factors, I commonly use up feet at baud manuall no issues. Lets finish the thread to make it helpful for manuxl that come after us. Manual says switches 4 and 5 set addressing mode.
Scripting must be enabled to use this site.
Backplane Current Load at 5V. Learning that the post I replied to was deleted makes me feel better – I thought I was truly becoming a grouchy old man! See link, appendix’s show the differences between series. Also, let us know the size of the chassis’ local and remote you are using.
Manuals On-line — I/O Library
We need the DIP switch settings all of them and the chassis sizes. SW2 ON allows the processor to restart the chassis But, with the PLC-5, we really don’t need your program. Does not matter which adapter I try with either processor.